CellarPro’s 4200VSi-220V 1/3 Ton Nominal cooling units are suitable for wine cellars up to 42 cubic meters in both commercial and residential wine cellars. The 42 cubic meter cellar size assumes that the cellar is constructed with insulation of R19 or better in all walls and ceiling (ie no glass or uninsulated concrete), the cooling unit is not ducted, a setpoint of 15C inside the cellar and ambient temperatures up to 29C outside the cellar.
CellarPro 4200VSi-220V / 50Hz Cooling Unit (P/N 1512). CellarPro engineered the 4200VSi 220V cooling unit to provide maximum cooling power and adjustable humidity control for cellars up to 42 cubic meters. Designed for internal installations that provide 187-254V power at 50Hz, 4200VSi 220V units are built with high-output Danfoss compressors and oversized coils for maximum performance in high-temperature environments up to 46C. These units also feature variable-speed fans with a low setting for super-quiet operation when conditions permit.
All air-cooled refrigeration equipment requires fresh air intake to dissipate the heat generated by the cooling unit. The fresh air intake CANNOT come from the wine cellar space – it must come from space outside the cellar.
This unit can be configured to operate in extreme temperature conditions (-29 to 46C). If the unit’s location does not provide sufficient room for airflow, you may need to purchase a rear duct kit.
Dual high-output centrifugal fans come with variable speed settings for your choice of maximum cooling power at the high fan speed, or super-quiet operation (53.7 decibels) at the low fan speed.
Adjustable humidity control combines a high-output compressor with flexible fan cycles to maintain a recommended level of moisture inside your cellar.
Extra-large coils generate maximum cooling power inside the cellar.
Excess condensate is managed with a high-capacity stainless steel drain pan, welded 1.27 cm drain line and 200W electric heating element with “On/Off” Control.
Commercial-grade Electrofin coating protects the evaporator coils from leaks and corrosion.
Intuitive LED display panel mounted on the evaporator with digital programmable thermostat is simple and easy to use. Remote thermostat is available as an upgrade.
Energy-saver mode, quick-chill mode, and auto-defrost cycle provide convenient solutions to common cellar needs.
Temperature set point range is 8.3C to 16.7C when the cooling unit is properly sized.
Unit operates with minimal vibrations and less noise than comparable units from competitors.
Audible and visual alarms and maintenance-needed indicator protect the cooling unit and the wine cellar.
Common dedicated 15-amp circuit is required to power the unit.
With dual power sources and a 3-meter power cord, the unit can be plugged into a receptacle from either the front or the rear of the cooling unit, providing flexibility for most installations.
Our easy-access disposable air filter protects the condenser coils and increases the expected useful life of the cooling unit.
Adjustable mounting brackets, included as standard equipment, ensure easy installation.
Removable steel case and refrigerant access valve provides access to the internal components for servicing and repair.
CellarPro’s 1-Year Standard Warranty, the most thorough in the industry, protects the unit against manufacturing defects.
Size:35 4/5w x 63 4/5d x 49 4/5h (cm)
Power/Rating:This wine cooling unit can be used in 187-254V environments at 50Hz. The power plug provided is Nema 6-15P 15A 250V Plug (Male). It has a screw cover plug housing with internal lug connections, and can be swapped easily to conform to local plug configurations. Compressor Amps:
– Common dedicated 15-amp circuit is required to power the unit.
– Running: 6.2 Amps
– Startup: 14.8 Amps
is ideal for smaller commercial and residential wine cellars and wine cabinets. TTW018 units are best suited for rooms up to 1500 cubic feet with limited glass and very good insulation. The TTW018 is easy to install and can be installed on your own without the support of a contractor. The max capacity of the TTW018 unit is 2,100 BTU/h (0.61 Kilowatts).
is ideal for small home wine cellars. TTW009 units are best suited for rooms up to 850 cubic feet with limited glass and very good insulation. This unit is also easy to install, and can be installed on your own without the support of a contractor. The max capacity of the TTW009 is 1,100 BTU/h (0.32 Kilowatts).
CellarPro's 3200VSi cooling units (1/3 Ton Nominal) are suitable for wine cellars up to 800 cubic feet in both commercial and residentialwine cellars. The 800 cubic feet cellar size assumes that the cellar is constructed with insulation of R19 or better in all walls and ceiling (ie no glass or uninsulated concrete), the cooling unit is not ducted, a setpoint of 55F inside the cellar and ambient temperatures up to 85F outside the cellar.
CellarPro's 4200VSi cooling units (1/2 Ton Nominal) are suitable for wine cellars up to 1,000 cubic feet in both commercial and residentialwine cellars. The 1,000 cubic feet cellar size assumes that the cellar is constructed with insulation of R19 or better in all walls and ceiling (ie no glass or uninsulated concrete), the cooling unit is not ducted, a setpoint of 55°F inside the cellar and ambient temperatures up to 85°F outside the cellar.
Quieter - Smaller - SmarterKOOLR MAGNUM
-Capacity max.: 900 cubic feet
-Through the wall type cooling system
-Don't be fooled by the low cost. This is the best system at any price!
Our wine cooling solution for keeping your wine at proper temperatures at the lowest cost possible so you can save the money for more wine to add to your wine cellar. With simple installation and use you can become professional wine collector. The wine cellar cooling units conveniently monitor the temperature inside your wine cellar, with digital display showing in adjacent room.
CellarPro 2000VS 220V / 50Hz cooling units (1/4 Ton Nominal) are designed for low profile installations in commercial and residential wine cellars up to 11.3 cubic meters. This cooling unit is designed for 220V / 50Hz environments only. It should not be used in 60Hz environments (eg North America).